To guarantee proper air suction, leave at least 15cm of space between the wall and the backside of the unit, where the carbon & dust filters and air inlet are located. At least 15cm of space should also be left between the topside of the unit and the ceiling. Larger spaces are preferred. The unit must stand free from the wall to avoid contact noises.
The unit can be hung from a ceiling or placed on a stand or frame.
To hang the unit from a ceiling, remove both side panels and pinch a hole through the insulation at the position of the 4 holes in the bottom of the unit. Use an M8 or M10 metal threaded rod with a nut, washer and rubber damper to prevent unwanted noise or vibration.
Stand or Frame
Make or buy a stand or frame to hold the weight of the Opticlimate. (see nameplate )You can use the rubber damper or a vibration damper (not incuded) Pinch a hole through the insulation at the position of the 4 holes in the bottom of the unit. Use an M8 bolt and washer to mount the rubber or damper.
Make sure the side of the condensation outlet is 1 cm lower than the opposite side.